Find great deals for Andover Controls Continuum NetController LL Cx Tac Inc.. Shop with confidence on eBay!. Andover Continuum™. Product Catalogue. Issue: October . Infinet NetController II CPU Module. Infinet NetController – Display Modules. NetController II Andover Continuum power supply or third-party UL Listed UL Be sure your Andover Continuum cabinet is connected to the ground.
||17 July 2012
|PDF File Size:
|ePub File Size:
||Free* [*Free Regsitration Required]
Andover Continuum NetController II – Feature Blast
After creation of network I learn controllers. Thanks you Very much. Do a “send to controller”. Send the controller to the SQL database this, should be fairly quick as there are no programs or points in the controller. Call your controls contractor.
Power Quality Pro’s Forum: I’m asking this question because I haven’t done it. All times are GMT Ping to the controller always didn’t lost. In same network we have other controller Andover CX with them we have not problems. Thanks for your help, as soon as possible i will try to do what you said. Version of Continuum is 1.
Please can you tell me what could be the problem???
If we evolve from the monkey then why are there still monkeys. Today i noticed, that actually the problem not only with the Net Controllers but with some Site Controllers But at a stage when I send blank controller to SQL database, in the anfover window i get error produced: I usually remark the error lines out until Netcontroler a clean import.
Building Science Discussions Pro’s Forum: Building Success with Routines and Rituals.
But I woul like to try them. Results 1 to 10 of 10 Thread: General Discussion Pro’s Forum: Training and Education Pro’s Forum: Sorry, one more question, how to send data to controller from text file?
Next create a new network controller, do a teach. Hello, I have a problem with Andover Controls Net controller: Ameya Hi Netcontrolller, I am new to the forum and I am looking solution for somewhat similar problem. Originally Posted by borias. There is an error in the stored SQL database for that controller.
Andover Controls Continuum NetController LL Cx Tac Inc. | eBay
I am using continuum version 1. I think that this is also database problem, because i think controller work in “NoDB” mode, but may be netcontrolelr wrong. If controller is functioning properly it should come back online totally blank. I could see my controllers online. If you get any errors during the text import, you will need to correct them. I only do this on controllers that have the problem Borias described.
I am very sorry, I’m not very good at English. The controller should be gone at this point. Borias, Andovsr your question about saving a text file I’m wondering if you have had any formal Continuum Training. It’s rare, difficult and time consuming to trouble shoot.
Andover Controls Net controller problem.
Andover Continuum NetController II – Feature Blast | Schneider Electric
I’ve seen this problem before. First you have to go to the Menu bar forgot the term at the bottom right and find the controller ICON. I hope you can help me solve this problem. If all is good at this point your controller is good. Valves, Regulators, Filters, Etc. Note the values of the errors and freemem system variables. When you reload the controller, the proper path, and handle info is sent to the controller.
This should reset the controller, wait for it to come back online, then send the system variables to the controller. I haven’t done what Autopilot has discribed.
Originally Posted by AutoPilot.